Emergency and Exit Lighting
According to NFPA 101, Section 7-9.3, ESC will conduct a functional test on every required emergency lighting system at 30-day intervals for not less than 30 seconds. In addition, we will conduct an annual test on every required battery-powered emergency lighting system for not less than 11/2 hours during which the equipment must be fully operational for the duration of that effort.
ESC also will do a visual inspection of all required exit signs, as covered by NFPA 101, 7-10.9.1, at intervals of no less than 30 days. In addition, ESC will conduct an annual test, under NFPA 72, 7-10.9.2, that includes the battery-operated emergency illumination source, where required in 7.10.4, in accordance with 7.9.3.